I've got a strange one when I'm on the TAsdo app on my phone. It says its heating though the temp is set lower than the temp in the house?
I have attached images.
Hope someone can help?
Dear Nicko - I am adding some examples of my system to demonstrate similar faliure issues:
Since your post is a month old I would like to add, that I have experienced these faliures mainly over the last month or so.
My hunch is it's a bad software / firmware / app update. Apologies in advance to Tado if it is due some external force.
GrayDav - Holla! - you may know me from other threads such as:
And to all reading - don't forget that a thread like this on the Tado forum will be marked "Answered" even if the replies are "mine is borked too"
Here's how to keep your question thread open:
Stay cool - HotPotato
I have experienced the same thing and have finally twigged what my problem is.
Hopefully it works for anyone else who has updated their Boiler and fallen into the same hole!
I changed from a Glo-worm to a Worcester boiler and kept my Drayton controller initially.
I then installed Tado which occasionally showed Heating to a temperature which was lower than the target!
If I switched to FROST PROTECTION and then Resumed the control it sorted the room out and SET TO was ON!
Today I noticed my problem! I found ZONE CONTROL and the device was identified as BRxyz which revealed itself as the DRAYTON controller - I REMOVED THAT DEVICE , the TADO software came back that my system was now on MANUAL , and it looks fine now (after 10 minutes).
I used to have the THERMOSTAT SUxyx in the lounge , plus a smart valve on the radiator and I thought they were figting each other all these months! I see I can CHANGE THE MEASURING DEVICE to SUxyz on the valve so I am happy! In fact I will use them is different rooms ifthey work as I hope! I will then try to set the ZONE CONTROL so the thermostat becomes the MASTER on-off point!
I have 10 radiators and only 4 smart valves so this has cost me a bomb because those 6 radiators are HOT whenever one of the 4 calls for heating!